Voltage Sag Mitigation in Fifty Bus System Using D-STATCOM for Power Quality Improvement
|International Journal of Electrical and Electronics Engineering|
|© 2017 by SSRG - IJEEE Journal|
|Volume 4 Issue 9|
|Year of Publication : 2017|
|Authors : Dr. P.V.Kishore, Prof. P. Parthasaradhy|
Dr. P.V.Kishore, Prof. P. Parthasaradhy, "Voltage Sag Mitigation in Fifty Bus System Using D-STATCOM for Power Quality Improvement" SSRG International Journal of Electrical and Electronics Engineering 4.9 (2017): 6-16.
Dr. P.V.Kishore, Prof. P. Parthasaradhy,(2017). Voltage Sag Mitigation in Fifty Bus System Using D-STATCOM for Power Quality Improvement. SSRG International Journal of Electrical and Electronics Engineering 4(9), 6-16.
The Distribution static synchronous compensator is capable of reducing the losses and improving the voltage regulation in Multi Bus systems. The Distribution static synchronous compensator injects a current into the system to reduce the losses. The Distribution static synchronous compensator is capable of enhancing the reliability and quality of power flow in low voltage distribution network. A Distribution static synchronous compensator is one of the new generation flexible AC transmission system devices with a promising feature of applications in power system. The Distribution static synchronous compensator is used to stabilize the system voltage by exchanging reactive power with the power system. This work deals with the modeling and simulation of Fifty Bus systems with Distribution static synchronous compensator and the voltage sag is created by involving a heavy load. The sag is mitigated with Distribution static synchronous compensator. The circuit models and simulation results are presented. Voltages at various buses with and without Distribution static synchronous compensators are presented. The simulation results are compared with the analytical results. Fifty Bus System with multiple STATCOMs is modeled and simulated. The improvement in voltage stability with Distribution static synchronous compensator is presented. Voltages at various buses with and without Distribution static synchronous compensator are also discussed.
 Ambra Sannino, Jan Svesson and Tomas Larsson (2003), “Power-electronic Solutions to Power Quality Problems” Electric Power Systems Research, Vol.66, Issue 1, July, pp.71-82.
 Anaya-Lara O. and Acha E. (2002), “Modeling and Analysis Of Custom Power Systems by PSCAD/EMTDC”, IEEE Transactions on Power Delivery, Vol. 17, Issue 2002, pp. 266-272.
 Ashwin and Thyagarajan, “Modeling and simulation of VSC based STATCOM”, iicpe06,pp303-307.
 Babri Ivoand Jones (2001), “A new three –phase low THD supply with High –frequency isolation and 60v/200A regulated DC supply”, IEEE.
 Baker, M.H., Gemmell, B.D., Horwill, C. and Hanson, D.J. (2001), “STATCOM helps to guarantee a stable system,” in Proc. IEEE-PES T&D, pp. 1129-1132.
 Bebic, J.Z. Lehn, P.W. Iravani, M.R. “The hybrid power flow controller - a new concept for flexible AC transmission”, IEEE Power Engineering Society General Meeting, DOI-10.1109/PES.2006.1708944, Oct 2006.
 Bhattacharya Sourabh, “Applications of DSTATCOM Using MATLAB/Simulation in Power System”, Research Journal of Recent Sciences, Vol. 1(ISC-2011), 430-433 (2012).
 Bilgin H.F., Ermis M. et.al (2007), “Reactive Power Compensation of Coal Mining Excavators by using a new generation STATCOM”, IEEE Tran. on Ind. Appl., vol.43,no.1,pp.97-110, Jan- Feb.
 Bollen, M.H.J. (2001), “Voltage sags in Three Phase Systems”, Power Engineering Review, IEEE, Vol. 21, Issue 9, pp. 11-15.
 Camzares. CA FL Alvarado, “Point of Collapse and Continuation Methods for Large AC/DC System,” IEEE TransactIons on Power Systems. Vol. 8, No. 1, Feb 1993, pp.1-8.
 Camzares. CA.FL Alvarado, CL. DeMarco, I. Dobson, W.F. Long. “Point of Collapse Methods Applied to AC/DC Power Systems,” IEEE Transactions on Power Systems, Vol. 7, No. 2, May 1992, pp. 673-683.
 Canizares, C A. Z T. Faur, “Arralysls of SVC and TCSC Controllers in Voltage Collapse,” IEEE Transactions on Power Systems, Vol. 14 No 1, Feb. 1999. pp 158-165.
 Carpita, M. and Teconi, S. (1991), “A novel multilevel structure for voltage source inverter,” in Proc. EPE, pp. 90-94.
 Chandrakar, V.K. Kothari, A.G. “Optimal location for line compensation by shunt connected FACTS controller”, The Fifth International IEEE Conference on Power Electronics and Drive . Systems”, Vol 1, pp 151-156, Nov 2003.
 Cheng, C., Qian, Crow, M.L. Pekarek, S. and Atcitty, S. (2006), “A Comparison of DiodeClamped and Cascaded Multilevel Converters for a STATCOM with EnergyStorage,” IEEE Trans. on Industrial Electronics, vol. 53, No. 5, pp.1512-1521,2006.
 Chun, L., Qirong, J. and Jianxin, X. (2000), “Investigation of voltage regulation stability of static synchronous compensator in power system,” in Proc. IEEE-PES, pp. 2642–2647.
 Deepika Masand, Shailandra Jain and ayatri Agnihotri (2008), “Control Strategies for Distribution Static Compensator for Power Quality improvement”, IEEE Journal of research vol.54,Issue 6, Nov-Dec.
 Del Valle, Y., Venayagamoorthy, G. K., Mohagheghi, S., Hernandez, J. and Harley, R. G. (2008), “Particle Swarm Optimization: Basic Concepts, Variants and Applications in Power System”, IEEE Transactions on Evolutionary Computation, April, 12, no. 2, pp. 171-195.
 Divya Sree, T. and Devi Shankar, M. (2015), “DSTATCOM with PI Controller for Voltage Sag Mitigation”, International Journal of Innovative Technology and Exploring Engineering (IJITEE) ISSN: 2278-3075, Volume-5 Issue-3, August 2015.
 EI Moursi, M.S. and Sharof, A.M. (2005), “Novel Controllers for the 48-Pulse VSC STATCOM and SSSC for voltage and Reactive Power Compensation”, IEEE Transaction on Power Systems, vol.20, no.4, Nov.
 Eldery, M. A., El-Saadany, E. F. and Salama, M. M. A. (2006), “Sliding Mode Controller for Pulse Width Modulation Based DSTATCOM”, Proceedings of Canadian Conference on Electrical and Computer Engineering, CCECE „06, pp. 2216-2219.
 Feng, Z. V. Ajjampu, D.J. Maratukulam, “A Practical Mimmum Load Shedding Strategy to Mitigate Voltage Collapse,” IEEE Transactions on Power Systems, Vol. 13, No 4, Nov. 1998, pp. 1285-129,
 Fuknda, S., Kanayama, T. and Muraoka, K. (2004), “Adaptiv e Learning based current control of active filter needles to detect current harmonics”, IEEE APEC.
 Giroux, P., Sybille, G. and Le-Huy, H. “Modeling and simulation of a distribution STATCOM using simulinks power system block set”, in proc. Annu. Conf. IEEE industrial electronic society, pp. 990-994.
 Gonzalez, P.G. and Cerrada, G. (2000), “Control system for a PWM-based STATCOM,” Trans. Power Delivery, vol. 15, no. 4, Oct., pp. 1252–1257.
 Greene, S. Dobson FL Alvarado, “Sensitivity of the Loading Margin to Voltage Collapse with Respect to Arbitrary Parameters,” IEEE Transactions on Power Systems, Vol. 12, No, 1, Feb 1997, pp. 262-272.
 Greene, S. 1. Dobson, F.L Alvarado, “Contingency Ranking for Voltage Collapse wa Sensitiwtles from a Single Nose Curve,” IEEE Transactions on Power Systems, Vol. 14, No. 1, Feb. 1999, pp. 232-240.
 Gyuayi, L. (1988), "Application characteristics of converter-based FACTS controllers, " in IEEE, vol. 76, no. 4, pp. 483-493.
 Gyugi.L, “Unified power-flow control concept of flexible AC transmission system‟: IEE Proc-C, Vol.139, No.4, 2000.
 Gyugi.L, Schauder.W, “The unified power flow controller: A new approach to power transmission control,‟ IEEE Trans., 2003, PD-10, (2).
 Gyugyi, L. (1998), “Understanding FACTS:Concepts and Technology of Flexible AC Transmission Systems”, Addison-Wesley, New York, pp. 135-207.
 Haque, M.H. (2001), “Compensation of distribution system voltage sag by DVR and D-STATCOM”, Power Tech Proceedings, IEEE Porto, vol.1, pp.10-13.
 Haque, M.H. “Optimal location of shunt FACTS devices in long transmission line‟, IEE Proceedings on Generation Transmission & Distribution, Vol.147, No.4, pp.218-22, 2000.
 Hendrimasdi, Nornanarivn and Bashi S.M. (2009), “Construction of prototype D-STATCOM for voltage sag mitigation”, European Journal of scientific Research, Vol.30, pp.112-127.
 Hendrimasdi, Nornanarivn S.M.Bashi,”construction of prototype D-STATCOM for voltage sag mitigation”, European Journal of scientific Research,ISSN145016*vol.30,Nov 2009,pp.112-127.
FACTS, D-STATCOM, UPFC, DVR.