Design of Shunt Active Power Filter for a Wind-Hydro Hybrid System Connected To Two Back To Back Converters with an Energy Storage Battery System
|International Journal of Electrical and Electronics Engineering|
|© 2015 by SSRG - IJEEE Journal|
|Volume 2 Issue 6|
|Year of Publication : 2015|
|Authors : N Raju khandavalli, G V Rammohan|
N Raju khandavalli, G V Rammohan, "Design of Shunt Active Power Filter for a Wind-Hydro Hybrid System Connected To Two Back To Back Converters with an Energy Storage Battery System" SSRG International Journal of Electrical and Electronics Engineering 2.6 (2015): 7-12.
N Raju khandavalli, G V Rammohan,,(2015). Design of Shunt Active Power Filter for a Wind-Hydro Hybrid System Connected To Two Back To Back Converters with an Energy Storage Battery System. SSRG International Journal of Electrical and Electronics Engineering 2(6), 7-12.
This paper presents the design of Shunt Active power filter and simplified control of hybrid system (wind –hydel) system connected to two back-to-back converters in which one is connected to hydel turbine and the other is connected to wind turbine system through squirrel cage induction generators (SCIG) feeding three phase loads in isolated locations. The main objective of this work is to provide a better control algorithm for the VSC and to achieve maximum power tracking (M.P.T) through rotor speed control of the wind turbine driven S.C.I.G under varying speeds at the machine side and to control the magnitude and frequency of the voltage at load side and to eliminate the ripple content in the wave forms and to create the system balanced. The system also ensures in sending the power generate by SCIGw is complete to the load through the load-side converter and remaining power be store into ESBS. And at the identical time if the required active power of the load is more than the total power generated by SCIGw and SCIGh. Then the deficit power is supplied by the ESBS. Simulation models of the proposed hybrid system with SAPF and the simulation results are obtained in MATLAB using Simulink and Sim Power System set toolboxes, with different load condition at different wind conditions.
 D.P Kothari, K.C Singal and Rakesh Ranjan, “Renewable Energy Sources and Emerging Technologies”, edition-2, pp.378-384.
 J. B. Ekanayake, “Induction generators for small hydro schemes,” IEEE Power Eng. J., vol. 16, no. 2, pp. 61–67, 2002.
 B. Fox, D. Flynn, L. Bryans, N. Jenkins, D. Milborrow, M. O’Malley,R. Watson, and O. Anaya-Lara, Wind Power Integration Connection and System Operational Aspects. London, U.K.: IET, 2007, ch. 3.
 G. Quinonez-Varela and A. Cruden, “Modeling and validation of a squirrel cage induction generator wind turbine during connection to the local grid,” IET Genre., Transmits. Distrib., vol. 2, no. 2, pp. 301–309, Mar. 2008.
 Burak Ozpineci and Leon Tolbert “Simulink Implementation of Induction Machine Model – a Modular Approach,” 0-7803-7817-2/03@2003IEEE.
 G.Quinonez-Varela and A.Cruden, “Modelling and validation of a squirrel cage induction generator wind turbine during connection to the local grid,” IET Gener., Transmiss. Distrib, vol. 2, no. 2, pp. 301–309, Mar. 2008.
 Tamas and Z.Szekely, “Modeling and Simulation of an Induction Drive with Application to a Small Wind Turbine Generator,” in Proc. IEEE Int. Conf. Autom., Quality Test., Robot., May 22–25, 2008, pp. 429–433.
 B.Singh and G. K. Kasal, “Voltage and frequency controller for a three-phase four-wire autonomous wind energy conversion system,” IEEE Trans. Energy Convers., vol. 23, no. 2, pp. 505–518, Jun. 2008.
 Bhim Singh and V.Rajgopal, “Digital Control of Voltage and Frequency of Induction Generator in Isolated Small Hydro System,” 2012IEEE International Conference on power Electronics, Drives and Energy System, vol.no1, pp 4673-4508.
 M. Aredes, E. H. Watanabe, New Control Algorithms for Series and Shunt Three-Phase Four-Wire Active Power Filters, IEEE Trans. Power Delivery, vol 10, no. 3, July 1995, pp. 1649-1656.
small-hydel, squirrel-cage induction generator (SCIG), MPT, Voltage Source Converter (VSC.), Shunt Active Power Filter (SAPF).